Ron Saunders of Fresh-Aire UV Joins us to Talk UV and More.
Michael Housh from Housh Home Energy Experts shares with HVAC School. This is an detailed demonstration of how to Make a Metal Duct Transition in the Field.
Checkout Housh Home Energy Experts: https://www.houshhomeenergy.com/
In our new series Bryan uses some resources from RSES NATE Prep to do some quick videos full of useful HVAC tips and data. In the first instalment Bryan discusses Motor Types.
Visit RSES website here: https://www.rses.org/
When you first start checking your supply air with a thermo-hygrometer you may notice that the relative humidity is REALLY HIGH. Often the RH in a supply duct will be between 85% and 96% relative humidity on a system that is functioning as designed. The reason for this is fairly simple.
In order for dehumidification to occur the air must reach dew point, otherwise known as 100% relative humidity
Jim Bergmann explains it this way. Think of a sponge being like air and when it is fully expanded it is like the air in the return. When the sponge is fully saturated and can accept no more water it is at 100% RH and when it is completely dry it is at 0% RH. Let’s imagine that the sponge is 50% saturated and full size in the return. When that sponge (air) goes over the evaporator coil it is compressed, because colder air can hold less moisture. Once that air is compressed (cooled) enough it will begin to give up moisture. This point at which it starts to give up moisture is called dew point or 100% relative humidity. Once that air leaves the coil it still remains in approximately the same temperature state (compressed sponge) as it was when it went over the coil. This means that unless heat is added or removed from that air, it will remain at 100% relative humidity.
So why is it less that 100% RH in the supply?
There are several reasons why the air in the supply will be slightly below 100% in the supply. First is contact factor or bypass factor which are both terms used to demonstrate the efficiency of a coil at “contacting” the air. The greater the surface area of the coil and the longer the contact time of the air on the coil the more efficiently heat will be transferred from the air to the coil.
Because no coil is 100% efficient, there will always be some air molecules that leave the coil warmer than others, this causes the airstream to be warmer overall and decreases the RH of the air stream. You will notice when a system has a higher coil air velocity (speed) it will have a higher bypass factor (lower supply humidity). When you run lower coil air velocity the bypass factor will drop and the supply RH will increase.
There is also some heat added by the blower motor and possibly even the cabinet or supply ductwork. This added dry bulb heat results in a warmer airstream and thus some additional moisture capacity. Imagine a slight expansion of the sponge due to heat from the duct walls and the blower motor.
Once that supply air exits the duct and mixes with the room air it is allowed to “expand” again and the relative humidity drops below what it was initially. This is why supply air has a high RH in cooling mode.
Here is a video we did on the topic –