When evacuating, the FASTEST way is to use two large diameter hoses connected to two core removal tools and the cores removed. These hoses are then connected to the pump using a tee or evacuation “tree”.
However, when you only have one large hose another acceptable method is to connect the large hose to the suction side and the vacuum gauge to the liquid side alone.
Brad Hicks from HVAC in SC made a nice little video showing how he does this with just one hose. He uses a core tool with the vacuum gauge on the liquid line to ensure that there aren’t and issues with depressing the core, which happens often with certain cores and gauge couplers. The other reason is so that he can valve off the vacuum gauge when he releases the charge or charges the unit to prevent refrigerant and oil from potentially entering his vacuum gauge.
The disadvantage of this setup is that the vacuum must all pull through the metering device which can add time to the process. In the case of a “hard shut off” TXV this method may not work.