This article is written by one of the smartest guys I know online, Neil Comparetto. Thanks Neil!
Recently I posted a question in the HVAC School Group on Facebook, “when designing a residential duct system what friction rate do you use?”. As of writing this, only one answer was correct according to ACCA’s Manual D.
So, what is friction rate?
Friction rate (FR) is the pressure drop between two points in a duct system that are separated by a specific distance. Duct calculators use 100′ as a reference distance. So, if you were to set the friction rate at .1″ on your duct calculator for a specific CFM the duct calculator will give you choices on what size of duct to use. Expect a pressure drop of .1″ w.c. over 100′ of straight duct at that CFM and duct size / type.
Determining the Friction Rate
First, you need to know what the external static pressure (ESP) rating for the selected air handling equipment is. ( external static pressure means external to that piece of equipment. For an air handler, everything that came in the box is accounted for, including the coil and typically the throwaway filter. For a furnace the indoor coil is external and counts against the available static pressure)
Next you have to subtract the pressure losses (CPL) of the air-side components (coil, filter, supply and return registers/grilles, balancing dampers, etc.). Now you will have the remaining available static pressure (ASP). ASP = (ESP – CPL)
Now it’s time to calculate the total effective length (TEL) of the duct system. In the Manual D each type of duct fitting has been assigned an equivalent length value in feet. This is done with an equation converting pressure drop across the fitting to length in feet (there is a reference velocity and a reference friction rate in the equation). Add up both the supply and return duct system in feet. It is important to note that this is not a sum of the whole distribution system. The most restrictive run, from the air handling apparatus to the boot is used. Supply TEL + Return TEL = TEL
The formula for calculating the friction rate is FR= (ASP x 100) / TEL
This formula will give you the friction rate to size the ducts for this specific duct system. If you test static pressure undersized duct systems are very common, almost expected. This is because a “rule of thumb” was used when designing the ducts.
This is just an introduction to the duct design process. I encourage you to familiarize yourself with ACCA’s Manual D and go build a great system!
— Neil Comparetto