- Tech Tips
Electronic leak detection is a critical part of any HVAC technicians common practice. Unfortunately, it is also one of the most common sources of misdiagnosis. Here are my tips to make your leak detection more successful.
Use Your Detector Second
Before starting to use your detector STOP! look for signs of leaks and corrosion throughout the entire system. I see so many techs who use an electronic leak detector with a very large leak when they would have been better served pressurizing and pinpointing the leak with soap bubbles.
Get a Good One
Use a good quality leak detector. Hint: If it costs less than $300 it probably isn’t great. I am fan of the H10G and the H10Pro although we are testing the Tifzx-1 as a possible option on the recommendation of a few good techs I trust.
Test Your Tools
Check your detector and make sure it actually works EVERY TIME. The H10G has a reference bottle for testing.. USE IT
Let it Warm Up
Many leak detectors require a warm up time for the sensor. With the H10G I allow it to run for at least 5 minutes before I start to use it.
Start at The Top
Most refrigerants are heavier than air, starting at the top and working your way down will help keep you from picking up a leak below the actual point of origin.
Move really slow and when you do get a hit, remove the wand, let it clear and go back to the same point a few times before calling it a leak. Once you think you found a leak, attempt to use bubbles to fully confirm.
Use Common Sense
No matter what leak detector manufacturers tell you.. there ARE other substances that can trigger your detector and refrigerant can move from one place to another due to drafts. I have seen several cases where chemicals in a garage are triggering the detector or where a tech has misdiagnosed an evaporator coil because of a chase leak where the refrigerant is being pulled from beneath the unit into the return. Look around and make sure there is nothing causing interference.
Before you condemn that coil BE SURE. Use all of your resources to positively confirm the exact location of the leak. A little patience goes a long way.
This podcast is a class that Bryan gave to some of the Kalos apprentices. The cover –
and Much More…
There are a few important things that I suggest checking on every service call to reduce callbacks and increase customer satisfaction. One of them that often gets missed is preventing wire rub outs.
One of my area managers and experienced tech Jesse Claerbout shot a video showing the simple step he takes to prevent major damage.
We also just release a new podcast episode today that you can hear in any podcast app or by listening HERE
In this episode of HVAC School Bryan talks to Leslie about the illusive TXV. They talk about:
And Much More….
In this episode of HVAC School we talk about thermodynamic basics, including:
And Much More…
In this episode of HVAC School I talk with my brother Nathan… and he just whines a lot about cool tools I like…
That’s basically all.
And we talk about solder rings and thermal imaging cameras and digital gauges.
In this episode of HVAC School we discuss the entire basic refrigerant / Compression refrigeration cicuit.
And Much More…