Grounding and bonding is important and it’s a fairly broad topic.
In HVAC/R we generally just need to make sure that we properly connect the conductors (wires) provided to the proper connection points in the equipment and occasionally the disconnects.
These connection lugs and / or green screws are rated for grounding so long as the system is “listed” by UL or another listing agency recognized by the NEC (National Electrical Code).
In other words, of you follow manufacture specs and diagrams you are in good shape.
There are some cases where we are tasked with making proper grounding connections when making repairs and when adding in accessories.
I’m going to encourage you to take more time when grounding rather than simply wrapping a wire around a random equipment screw and calling it a day.
There are practical and code reasons for this, but one of the most compelling reasons is you don’t want to have been party to an injury caused by poor grounding.
Now for the code reasons.
The National electrical code wants us using grounding connections listed and designed for that purpose or making sure that we use screws that have
At least two threads engaged or a nut connected on the opposite side
And this can be tricky to accomplish when connecting to sheet metal.
Let’s take a look at exactly what the code (NEC NFPA 70® 2017) has to say –
250.8 Connection of Grounding and Bonding Equipment.
250.8(A) Permitted Methods.
Equipment grounding conductors, grounding electrode conductors, and bonding jumpers shall be connected by one or more of the following means:
Listed pressure connectors
Pressure connectors listed as grounding and bonding equipment
Exothermic welding process
Machine screw-type fasteners that engage not less than two threads or are secured with a nut
Thread-forming machine screws that engage not less than two threads in the enclosure
Connections that are part of a listed assembly
Other listed means
One of the most common disputes about grounding involves the type of screws used so let’s take a quick side path to address that.
Take a look at the threads on each of these screw types. You will notice that the thread cutting (forming) and traditional machine screws have a fine thread with a less aggressive pitch while the drilling and tapping screws are designed to be “driven” into metal.
The NEC mentions a “machine screw” but the definition of what exactly is and isn’t a machine screw can vary so we won’t use that alone to exclude self drilling, self tapping and equipment screws.
We know that traditionally when someone says a machine screw they are talking about the finer threaded screw that can accept a nut and obviously there is no way to put a backing nut on any “drilling” type or typical HVAC equipment screws.
It all comes down to the thickness of the the metal and how many threads are engaged. This is why many equipment grounding screws are set into an extrusion or dimple in the metal and the screw is tapped into it.
When you are in a pinch you can always use a machine screw and a backing nut and the NEC says you are fine. You will notice in section 250.8 there is nothing about the screw needing to be green… so at least you can save on green paint.
It was pointed out to me after I wrote the initial article that there IS a section about the equipment grounding screw needing to be green or marked. Thanks to Michael Labanz for pointing out this section
250.126 Identification of Wiring Device Terminals.
The terminal for the connection of the equipment grounding conductor shall be identified by one of the following:
A green, not readily removable terminal screw with a hexagonal head.
A green, hexagonal, not readily removable terminal nut.
A green pressure wire connector. If the terminal for the equipment grounding conductor is not visible, the conductor entrance hole shall be marked with the word green or ground, the letters G or GR, a grounding symbol, or otherwise identified by a distinctive green color. If the terminal for the equipment grounding conductor is readily removable, the area adjacent to the terminal shall be similarly marked.
Informational Note Figure 250.126 One Example of a Symbol Used to Identify the Grounding Termination Point for an Equipment Grounding Conductor.
Bryan Orr is a lifelong learner, proud technician and advocate for the HVAC/R Trade