The most common and often most frustrating questions, that trainers and senior techs get goes something like this. “What should my ______ be?” or “My _____ is at ______ does that sound right?
Usually, when the conversation is over both the senior and junior techs walk away feeling frustrated because the junior tech just wanted a quick answer and the more experienced tech wants them to take all of the proper readings and actually understand the relationships between the different measurements.
In this series of articles we will explore the, “What should my _______ be?” questions one at time and hopefully learn some things along the way.
So what should the superheat be?
First, what is superheat anyway? It is simply the temperature increase on the refrigerant once it has become fully vapor. In other words, it is the temperature of a vapor above it’s boiling (saturation) temperature at a given pressure.
The air around us is all superheated! Head for the Hills!
How can you tell that the air around us is all superheated? Because the air all around us is made of vapor. If the air around us were a mixture of liquid air and vapor air, first off you would be dead and secondly, the air would be at SATURATION. So the air around us is well above its boiling temperature (-355° F) at atmospheric pressure which means it is fully vapor and SUPERHEATED. In fact, on a 75-degree day, the air around you is running a superheat of 430°
But why do we care?
We measure superheat (generally) on the suction line exiting the evaporator coil and it helps us understand a few things.
#1 – It helps ensure we are not flooding the compressor
First, if we have any reading above 0° of superheat we can be certain (depending on the accuracy and resolution of your measuring tools) that the suction line is full of fully vapor refrigerant and not a mix of vapor and liquid. This is important because it ensures that we are not running liquid refrigerant into the compressor crankcase. This is called FLOODING and results in compressor lubrication issues over time.
#2 – It gives us an indication as to how well the evaporator coil is being fed
When the suction superheat is lower it tells us that saturated (boiling) liquid/vapor mixture is feeding FURTHER through the coil. In other words, lower superheat means saturated refrigerant is feeding a higher % of the coil. When the superheat is higher we know that the saturated refrigerant is not feeding as far through the coil. In other words higher superheat means a lower % of the coil is being fed with saturated (boiling) refrigerant.
The higher the % of the coil being fed the higher the capacity of the system and the higher the efficiency of the coil.
This is why on a fixed orifice system we often “set the charge” using superheat once all other parameters are properly set. Adding refrigerant (on a fixed orifice / piston / cap tube) will feed the coil with more refrigerant resulting in a lower superheat. Removing refrigerant will increase the superheat by feeding less of the coil with saturated (mixed liquid and vapor) refrigerant.
This method of “setting the charge” by superheat does not work on TXV / TEV / EEV systems because the valve itself controls the superheat. This does not negate the benefit of checking superheat, it just isn’t used to “set the charge”.
#3 – We can ensure our compressor stays cool by measuring superheat
Most air conditioning compressors are refrigerant cooled. This means that when the suction gas (vapor) travels down the line and enters the compressor crankcase it also cools the motor and internal components of the compressor. In order for the compressor to stay cool, the refrigerant must be of sufficient volume (mass flow) and low temperature. Measuring superheat along with suction pressure gives us the confidence that the compressor will be properly cooled. This is one reason why a properly sized metering device, evaporator coil, and load to system match must be established to result in an appropriate superheat at the compressor.
#4 – Superheat helps us diagnose the operation of an active metering device (TXV / TEV/ EEV)
Most “active” metering devices are designed to output a set superheat (or tight range) at the outlet of the evaporator coil if the valve is provided with a full liquid line of a high enough pressure liquid (often at least 100 PSIG higher than the valve outlet / evaporator pressure). Once we establish that the valve is being fed with a full line of liquid at the appropriate pressure we check the superheat at the outlet of the evaporator to ensure that the valve itself is functioning properly and /or adjusted properly. If the superheat is too low on a TEV system we would say the valve is too far open. If it is too high the valve is too far closed.
#5 – Superheat is an indication of load on the evaporator
On both TEV / EEV systems and fixed orifice systems (piston / cap tube) you will notice that when the air (or fluid) going over the evaporator coil has less heat, or when there is less air flow (or fluid flow) over the evaporator coil the suction pressure will drop. However, on a TEV / EEV system as the heat load on the coil drops the valve will respond and shut further, keeping the superheat fairly constant. On a fixed orifice system as the load drops so will the superheat. It can drop so much on a fixed orifice system that when the system is run outside of design conditions the superheat can easily be zero resulting in compressor flooding.
When the load on the evaporator coil goes up a TEV / EEV will respond by opening further in an attempt to keep the superheat constant. A fixed metering device cannot adjust, so as the heat load on the coil goes up, so does the superheat.
When charging a fixed orifice A/C system you can use the chart below to figure out the proper superheat to set once all other parameters have been accounted for or you can use our special superheat and delta t calculator HERE
Using this chart requires that you measure indoor (return) wet bulb temperature so that the heat associated with the moisture in the air is also being accounted for as well. This is one of MANY target superheat calculators out there, you can use apps, sliderules etc… Here is ANOTHER ONE
Remember, this chart ONLY applies to fixed orifice systems.
So what should your superheat be in systems with a TEV / EEV? The best answer is… like usual… Whatever the manufacturer says it should be.If you really NEED a general answer you can generally expect
High temp / A/C systems to run 6 – 14 degrees of superheat
Medium Temp – 5-10
Low Temp – 4-10
Some ice machines and other specialty refrigeration may be as low as 3 degrees of superheat
When setting superheat on a refrigeration system with any type of metering you often must get the case / space down close to target temperature before you will be able to make fine superheat adjustments due to the huge swing in evaporator load. Once again, refer to manufacturer’s design specs.